Eurotherm temperature controller Edit Subject. Join us on Facebook. I gues there was no easy way around this. Thank you for the last advice. However, i am not able to communicate with with my itools or labview. I have an issue communicating with a eurotherm temperature controller configured in modbus TCP. Adrian How does this make you feel?
|Date Added:||23 February 2006|
|File Size:||49.89 Mb|
|Operating Systems:||Windows NT/2000/XP/2003/2003/7/8/10 MacOS 10/X|
|Price:||Free* [*Free Regsitration Required]|
I’ve tried running one meter at a time, using the datalogger provided by the meter company, and see similar results.
I have attached an example file for testing, the vi request the current PV register address 1 from the eurotherm. Eurotherm temperature controller Edit Subject. Could it come from too high of a latency of the instrument or something else?
However, i am not able to communicate with with my itools or labview. Eurotherm iTools software for configuration and monitoring of temperature controllers and recorders Eurotherm iTools is a versatile suite of software tools to allow configuration and monitoring of Eurotherm temperature and process controllers, power controllers and recorders.
The error explanation I get is:.
NI Labs Discussions
Message 3 of And then it all worked fine after that. Could you please tell me how to locate property nodes. Also where should I plug in connection cable for it to communicate with computers? Message 6 of Create a new topic About this Question 3.
NI LabVIEW Modbus API Discussion – Page 43 – Discussion Forums – National Instruments
Overview Topics Products People Change log. Log in or Sign up.
Hi friends, anyone already used micrologix with this library? Thanks for your answer, is it sufficient to add it right after the opening of the TCP connection, as in the picture of the diagram attached I’m testing this right now?
Load a uip file to Eurotherm using Labview (directly or indirectly)
You can invoke the Eurotherm Stand Alone Setpoint Programmer with the following command line arguments: The computer and the eurotherm are connected with a cross-over ethernet cable for the connection.
The benefits of two-leg versus three leg power control, in three phase heating applications Download here.
I manage to get the connection, but only for a limited time, after which I get an error 56, with the following message indicated at lahview end of this post. All Forum Topics Next Topic. John How does this make you feel?
Hope that helps, Adrian How does this make you feel? If the lack of this call is the problem, then I don’t understand why it would work without that for some time and then shut down every so often. I’m not too familiar with neither the modbus protocols nor the API though I’ve read quite a bit about it since I’ve had to setup communication with that eurotherm.
You should not delete the property nodes, rather you should have replaced with some other code which is relavant to ethernet communication.
Does that mean that for and the controller can only intake one thermocouple input? Message 9 of You might be interested in Adrian Oliver Employee February 23, Customer support Technical helpdesk. You could manually extract the data from the UIP file, but you would have to match the program segment parameters to their respective MODBUS registers note that they may change between versions ofthen write those values directly into the device.
Eurotherm iTools is a versatile suite of software tools to allow configuration and monitoring of Eurotherm temperature and process controllers, power controllers and recorders.
I have 2 versions of configs and i need to compare it between each other.